Fire extinguisher inspection requirements a standard feature in many buildings and private homes. One way to help ensure the fire extinguisher will work properly when needed is to follow the schedule mandates the federal government inspection. This inspection recorded on the hang tag attached to each fire station. Also, to the list of the inspection and the date on which they made, the inspection tag usually includes a description of the fire service, including the model number.
Fire extinguisher inspection requirements
Check to make sure it contains the latest and accurate information is an important element of building safety inspection. Because this situation is unique, it is very important that each room prepared with the correct fire extinguisher inspection requirements.
OSHA 29 CFR 1,910,157 regulations set requirements for portable fire extinguishers. Then, testing and approvals for fire extinguishers carried out by Global FM and listed by Underwriters Laboratories.
Fire extinguisher inspection requirements classified by types of fires they put out.
Type A was for Gomi like wood, plastics, and paper.
Class B is for flammable liquids such as oil, gasoline, and chemical.
Type C is to fire electrically conductive.
Class D fire extinguishers are for flammable solids such as sodium and magnesium.
Type K fire extinguishers specific to commercial applications.
After the fire extinguisher inspection requirements listed by UL, UL ratings it, such as the 4A: 20B: C. A rating is the water of equity. Then, each the equivalent of 1.25 gal water. 4A = 5 gal. water. B:C rank is similar to the amount of square footage. Also, associated with the level of experience of the operator, the fire extinguisher can cover. 20 B:C = 20 square coverage.
OSHA requires companies to select and distribute fire extinguishers that based on the grade at work anticipated fire and also on the size of the dangers that will affect their use. The company must give the employee a firefighter training When they hired and re-train every year. Fire extinguishers have to inspected monthly per OSHA standard 1910.157.
Observation and maintenance of fire extinguisher inspection requirements:
1. should remain in operation and filled. 220.127.116.11. the OFC
2. must be located so that they are easily visible and accessible at All times 18.104.22.168 (1) OFC
3. Have the defects must be repaired when necessary 22.214.171.124. NFC & 126.96.36.199. OFC
4. Inspect all fire extinguishers and also record inspection date on the back of the tag. 188.8.131.52. OFC
5. Ensure that the body not tampered and not damaged.
1. Nozzle for obstruction
2. Seals indicators are in place
3. Gauge pressure reading within the range of operating
4. no signs of physical damage
5. Operating instructions legible nameplate
6. Access and visibility is not obstructed
7. A monthly inspection should be more frequent if there is one of the following:
a) High frequency of fires
b) Dangers of weight
c) Vulnerability for disruption
d)The possibility of the theft of fire
e)Location that makes extinguishers exposed to mechanical injury. NFPA 10 184.108.40.206.
Every year fire extinguisher inspection requirements
1. Every 12 months the fire extinguisher element basis of antifreeze types. NFPA 4.5
2. All fire extinguishers required after marked by inspection. Also, after fire extinguisher maintenance. NFPA 4.5
3. All fire extinguishers should be examined to hydrostatic test intervals. However, the test pressure shown on the nameplate Fires NFPA 220.127.116.11.